Connecticut Application to Connect
In this section you will find information pertaining to the safe interconnection of generators to the Eversource power system.
Such interconnections include photovoltaic arrays (solar panels), wind turbines, cogeneration units and micro turbines, to name a few. All guidelines and fees have been filed and approved by the State of Connecticut Public Utilities Regulatory Authority (PURA).
Answers to frequently asked questions is also available.
Interconnection Application Options
|Residential Inverter-Based Generators 20 kW or less
|Fast Track: Residential Inverters greater than 20 kW; Commercial & Industrial less than or equal to 2 MW
|Study Process: Complex projects greater than 2 MW
Per PURA Docket No. 03-01-15 RE02 (Compliance Order No. 1, May 12, 2010 Attachment 1) and PURA Docket No. 03-01-15 RE03 (Guidelines for the Interconnection of Residential Single Phase Certified Inverter-Based Generating Facilities of 20 kW(ac) or Less) the Connecticut Electric Distribution Companies (EDCs) “are responsible for the distribution of electric power throughout most of the State of Connecticut. In order to carry out their responsibilities to all customers, each EDC must assure that all Interconnections are made to certain protocols and procedures, which are described in these Guidelines.”
Please read the guidelines (above) and technical requirements to understand how your generating system needs to be installed to meet federal, state and local electrical codes.
One line electrical schematics
Key elements to illustrate are:
- The utility voltage at the main panel (three- or single-phase).
- The fuse symbol and size at the main panel feeding the inverter.
- The number and location of inverters with the manufacturer's name, the model number, and rating.
- Indicate circuit connectivity from the main switch, including sub-mains (if applicable), metering, the main switch and the rating of breakers.
- The location of the isolation device.
- Title Block that includes but is not limited to, customer's name, address, and revision number of drawing if applicable Conventional symbols should be used to illustrate the inverters, circuit breakers, switches, fuses, etc. Please refer to the Information & Requirements for Electric Supply Below 600 Volts (PDF).
- Sample One Line Diagram (PDF)
- Sample One Line Induction Generator (PDF)
- Sample Three Line Diagram (PDF)
- The location of the site structures, metering and transformers.
- The location of the AC Disconnect Switch with relationship to the Eversource meter.
The EDC requires that the isolation device be visible and in close proximity (10 feet or less) to the main utility panel. It must be clearly identified if the AC Disconnect Switch is not located within 10 feet of the meter. Variances must be approved in writing.
Refer to Section 4.4 of the Residential Inverter-Based Generator Guidelines and Exhibit B in the Fast Track & Study Process Technical Requirements for more information.
Proof of insurance
- Policy carrier
- Policy number
- Policy effective dates
- Applicable minimum limited liability
||$300,000 - $2 million
||Actual Cost Based
||$2 - $5 million
* Please note time is measured in business days.
||Minimum Liability Insurance Required
|Greater than 0 kW to 100 kW
|Greater than 100 kW to 1 MW
|Greater than 1 MW to 5 MW
|Greater than 5 MW
Technical specification documents (data sheets)
Important Documents & Links
Applications, fees and documentation can be mailed to:
Attention: Eversource CT DG
P.O. Box 1409
Hartford, CT 06143-1409
Applications and documentation can be emailed to: